Type: Posts; User: PlatinumRH
I also recently saw a demo. Anyone tried using the DG Box to talk straight to BACnet controllers?
Unless you are having major performance problems I wouldn't do it. I've seen older computer get completely hosed up when attempting a defrag. At the very least I would back up the computer before...
You would need the Alerton Envision software, and a copy of Microsoft Visio to really be able to program the Alerton controllers. I don't think you'd have to have a BCM if you used the Jace as your...
I second what Matrix said. Virtual XP mode is the only way I've gotten FX Builder to work on Windows 7.
I am using gmail for my SMTP on 2 different AX sites with no problems. I use port 465 with SSL enabled.
Histories aren't a problem if you set them up to archive in the Server. The ORD for the history in the Jace is the same as the ORD for the archived history in the Server. For example:...
If all you have under tools is application lookup then its definitely the privileges of the account you are signing in with. The Alerton rep should be able to get in there and change that for you.
Sentry, I am pretty sure the "_" is not a special character and you don't need the "$5f", just an "_"
I sent you an email to the address in your profile.
I don't have the Honeywell ax wizard jar. We just need to pull in the points, not any programming. Do I need the wizard jar to get the points? The NVs I learned don't match what I am seeing in the...
Is there a Hwell XL15C shadow object/jar file in the palettes somewhere? I've looked and can't find one. When I did a discover on site it came in as a Dynamic Device with a bunch of NVs that don't...
Can I get the .xif file using the R2 Jace and convert that file to an .lnml file to use with my AX station? Anyone know or done this before?
Yeah, it was a dynamic device in the R2 Jace also. I was hoping I was overlooking it somewhere since I could do a lot more work offline if I had the device. Thanks.
If there are an time delays in the program then you definitely need to put equipment in hand. They reset when DDC is sent to the controller.
Does anyone know if there is a MNL 800 device/shadow object for Tridium AX? I am upgrading a site from R2 to AX and don't see it in the LonSiebe palette or anywhere else?
Can you email me what Landis & Staefa you still have, if any? Thanks.
Did you check to see if the points are "out of service"?
pault is correct. You would need Alerton's Envision for Ibex software and an Alerton USB or parallel port key. You would also need a cable to connect directly to the microview.
We've had sucess with export tags. This way you can house the graphics on both the Jace and the Web Sup. If the Web Sup goes down, then you can access the Jace directly for the graphics.
The BCM-ETH and the MS/TP controllers have different network numbers. Make sure you are scanning all networks when do the discover and that your jace network number is different.
Try the PxInclude widget in the bajaui palette
frontline, check your email address that's in your profile
When you go to first install it you should have the option to choose the full version or the commissioning only version. Make sure you installed the full version.
For anyone else with the same problem I finally found the solution. All of my AX installations were 32-bit. I tried uninstalling one version and re-installing it at 64-bit. As soon as I did this...
I am interest also! Thanks.