Type: Posts; User: Balkandroid
Search: Search took 0.00 seconds.
You have to upgrade the database thru Quick Builder. (You must to have .pjt file from the DDC, and from the CARE software export the file). Whatever, you should have enought access level in the...
For me more then one day.....still not received the approve.
First go to one of the DDC controllers where is communication with EBI working, and read-out thru the MMI the correct baud rate, then go to the controller where is the starts (***), and set...
I have registred to forum 11-25-2008, but now I have recognized, that I have missed the introduction :whistle:
Since 2008 I have found many helpfully posts and some problems I have solved with...
03-17-2013, 06:23 AM
I have found in my "old catalogues and datasheets" archive complete documentation for TEC (november 1997), maybe you can use - for example - the "TEC Parameter Description" CM2A3615E10, but this is...
Sorry, I have missed the MMI access code, the right code is: 6667
Please check the C-BUS communication settings by XI582AH (MMI). The Baud rate and the controller C-BUS address.
The full access to the system is (password in the MMI) is : 5556
Drafty888, my opinion is same as Sysint, the Loytec have now the best solutions on the market.
We have use it (LON<->BACnet) in one project (we have previously no experience with Loytec or similar...
By my optionion - yes, but the Care will ask you will you upgrade the pjt file to newest version.
I have it, but cannot find your e-mail address.
However, it's need a dongle to use it.
We have faced with similar problems (as you have described) few times, and the final result was - unfortunatelly - replacement of N30.
This symptom is occured only with the latest N30 controllers...
Results 1 to 11 of 14