Type: Posts; User: acguy951
Search: Search took 0.01 seconds.
11-02-2012, 11:25 AM
Mrak, tell me some more about your particular experience with the Mcquay unit you referred to?
11-02-2012, 11:23 AM
Mrak: We got the oil analysis back indicating minimal moisture, high acid, high aluminum high iron and silicon. Mcquay just sent us 2 more compressors. Had a quality assurance guy come out from...
10-20-2012, 12:54 PM
The compressor oil level was half way when they were off. While running one compressor the sight glass was full when both compressors run they both are below the halfway mark on the sight glass. Oil...
10-20-2012, 11:53 AM
I plan on doing oil analysis on monday. I did drain some oil. That was when I noticed the color. The RLA are 58 amps. Changing the oil in the compressors is going to be my first attempt at saving...
10-20-2012, 11:35 AM
Having a problem with copeland tandem scroll compressors. The compressors are over amping and tripping breakers in machine. They will run but the amps at startup are 100 + then fall back to 60 amps...
Results 1 to 5 of 5