Is this not the same plant, where you also changed the evap fan operation, to a forced draft off cycle defrost. (original fan control was off with thermostat)
Originally Posted by Mechanicalman1
Is also the same plant that had a very small hysteresis on the air thermostat control, along with no anti cycle settings.
So a simple change to the control algorithms, would achieve the same results for next to little to no cost.
Milking more oil from snakes "I think"
Hah, entertainment at its finest...