Enviro-Tec HLP 40 FCU
I have an Enviro-tech fan coil unit that I am trying to figure out the drain pan situation. These units have oversized insulated drain pans that catch the condensate. But from what I can see the bottom of the coils have a sheet metal covering. This cover has condensate drops all over it on the ends where I can see. Is there supposed to be a hole out in the middle of this cover? Of all of the units that I have looked at, I cant see above the large drain pan and under the coils. These installs are so tight I can't get my head up there and can't see anything with a mirror. I am not removing humidity and I think the condensate is getting blown into the air stream.
Any help appreciated.
Hi, Just wondering how you solved this problem? I have the same problem with water getting in the air stream with these units.
What I finally found was there are oblong drain holes in the downstream side of the drain pan that get clogged. Getting to them is another story.