Originally posted by davidr
That static regain connection causes people some fits on those little air handlers. :DQuote:
Originally posted by karsthuntr
If you have units that need a different charge for Heat and cool than there is something wrong. All Rheem/Ruud have accumalators on there HP's.Quote:
Originally posted by bornriding
Excuse me if I am off base here, but is this a heat pump and does it have an accumulator?? If it is a HP and no accum. then it may just have to be charged differently for heat & cool. Probably a Rheem or Rhuud ???
When I find this problem it is usually because the airflow is not correct.
For some reason Rheem/Ruud has a bad rep because it is not very forgiving. Most of the time the install instuctions were not followed and it's an install error.
Or lack of.