System Performance Update
Here in Chesapeake Va today high 87 degrees. Currently 86 degrees and 63 RH.
Thermostat set at 72 and inside RH is 38
Register temp at closest to airhandler 57 degrees
Register temp farthest from air handler 60 degrees
Attic Airhandler return air intake plenum 72 degrees
Attic Airhandler 12 foot supply plenum 4 feet from airhandler 55 degrees
Attic temp is 90
Scroll Compressor still seems noisy inside the house but normal outside??
Laser thermometer temp of compressor top near liquid line is 175 degrees. Sides and rest of compressor is relatively cool.
Opinions other than go to the Beach :)