If air is not an issue you may want to check for restricted heat exchangers as well. In the event that the heat exchagers begin to plug up the temps and pressures may increase. Do all the other checks. Absorbers just suck no matter who made them, thus the vacuum.
Not really an absorber fan as you may note.