Goodman 13 Seer Heat Pump
This was Posted Earlier but was moved
New Install--Outside unit and AHU--Heat Pump
10 Degree Slit on Air Temp inside-Ret and Supply
Superheat 10 Degrees--Tried Adjusting Charge--Superheat stayed 10 either way
Unit not Cooling Properly--Need 15-18 Degrees across Evap Coil.
R-22 System--Piston Metering Device.
Goodman 13 Seer Not Cooling
The Unit has been Repaired--Due to a Leak on Installation--Too much Refrigerant was added back--Weighed in Charge and Now--15 Degree Superheat and 15 Degrees across Coil--10 Degree Subcooling--Thanks For all your Help!!!