Carrier Infinity troubles
I have a Bryant furnace, ac and infinity thermostat.
Since day one the ac was unable to provide me with sufficient cooling on hot days. I tried to increase the cfm by using the dip switches on the furnace board, and now the thermostat is locked out saying service required, and the furnace board is flashing code 25, which seems to indicate equipment missmatch. I returned the dip switch back to original but the fault will not clear. The condensor would run without the blower coming on. I installed a honeywell t-stat that I had and rewired to work as a normal furnace would. All is well but I really want the Infinity to work. Has anyone encountered this problem?