JCI - FEC / NCE pulse
Can anyone shed light on if the JCI - FEC and NCE use a certain BI point for a pulse meter.
I know that in the N2 product line, you can use DI2 (CNT2), and BI4 for the DX9100 and UNT. Can't really find anything online for the FEC or NCE.
FEC/NCE only uses the BIs for pulse inputs not UI's
It has to be a BI and it has to be assigned as accumulator object in cct.
Originally Posted by berg2666
Thanks - that's the part I was missing.
Originally Posted by MikeAdams