Attachment 335341Attachment 335351Attachment 335361Attachment 335371Attachment 335381Attachment 335391
Just a little side job.. All new copper and drainline inside and out. duct work and the whole 9 yrds
where does the vent pipe from the trap go?
tubing looks good outside.
No clean out for the trap? Good thing you added a float switch cause it's gonna need it without a clean out on that trap. :)
Put the drier inside. Never rust out in the house..
Outdoor service outlet, nice.
So, if you're not terminating the vent for the drain above the level of the float switch, what happens when the drain clogs downstream of the vent? The water pours out of the vent before it has a chance to trip the switch. We always terminate above the height of the primary pan, even if it means drilling another hole in the deck.
good point i always make sure to do that with units in hung cielings, guess i didnt think about it too hard under the deck