Trane RTHB term. leak
Have a Trane RTHB215 that is leaking trough one of the compressor (CHHA) electrical terminal. Does any of you know where I could find a manual on how to change this seals if it coul be change and where I could find them. Any help will be appreciate it. Thanks..
You can find general guidelines in RTHA SB 15. (I canít send it, I have only hard copy) Donít open unit without it.
The rear cover of motor, which holds the economizer plate, must be removed.
About parts it is better to contact TRANE nearest office with full model and serial number of compressor and unit in order to have the parts.
If leak is between the white ceramic and copper stud check with TRANE office if you can use KIT06841 which is used in CHHC compressors. This KIT will not work if you have cracked ceramic. (PART SVN07A EN)
I could try to give you part numbers if you send me by email full model numbers.
Sorry for not be so helpful,
You have been of great help already CV ,Thanks. I will get Model and serial # and get back to you,Thanks again.where can I get your email,mine is in my profile. CS
see if this attaches never mind cant get stupid thing to attatch, I will send you that sB
that should be what you need
I got it , Thanks a lot ,r404a. CS