Attachment 332931 dryer looks like cement!Attachment 332941 these chunks were between the condenser and the dryer BEFORE the filter screen! Cap tube looked the same as the dryer for about 6-8 inches.
can't see the pictures.
But from the sounds of it...
Sounds like someone put in a lot of leak sealant into a system with moisture.
sent from my Samsung Galaxy Note
POE after dirty cond coil or bad cond fan mtr cooked it? Way way too common.
I see the pics fine on my phone. Can you guys not see them?
I can't see the images.
It's just blue text that says "Attachment 332931" & "Attachment 332941"
When I click on it. It says it's an invalid attachment.
Take a pic of the phone a post it:grin2:
Looks like you got yourself a meth lab.
Never seen anything like that. Could that be the dessicant from the drier? Maybe something in the drier ruptured?
Wax and POE.
A friend of mine had an employee of his working on a lawyer's package unit. He was changing out the compressor and installed the LL dryer on the hot gas line. It ran fine for 2 or 3 months before the dryer came apart inside and stopped up the system. The material in your system looks like desiccant beads to me.
That is what a drier that was working suppose to look like. It was asked to do more that's when the unit quit.