OK, so is Ultra Aire a good brand? Seems like everything is junk these days....
If I install one with ductwork in the attic, how much heat is it going to produce running the air through this duct...is that an issue? I know if you spray foam the attic this would be ideal.
If you interlock to AHU blower with the unit, then you will have some more heat gain. If comfort is the goal, how do you overcome these things?
Ultra-Aire is the highest efficiency whole house dehumidifier available today, 4-8 pints per KW. The heat is 1,050 btus per pint of dehumidification plus 3,414 btus per kw used. This means minimal heat generated. These units have enough fan power to move dry air throughout the home with the dehus fan via the a/c's ducts. Do a return to the dehu from the open part of the home. The dehus supply is connected to the a/c supply. When the dehu operates dry is circulated without the a/c fan.
Originally Posted by ChaseAir
The dehu is not needed when the a/c is operating, only during low/no cooling loads.
Thanks, my home system seems to need dehum even with the Infinity 2 stage running in the summer. Our humidity is crazy and I am weary of the floor model dehum. Nice to know it can do the job without the fan running, that was a concern.
Originally Posted by teddy bear