Originally Posted by hvacvegas
Looks nice and clean.
Before you finish though, is it still possible to increase the distance of straight pipe going into your air seperator.
Those models need about 18" of straight pipe for laminar flow, so the air seperates from the water, and allows the scoop to "scoop" it up.
Oooo, one of those little things. Nice to know.
True for Spiro too?
I don't think that rule applies to spiro.
Sent from my iPhone using Tapatalk