What a difference 25 deg ambient makes
Revisited this system today to replace cooked run capacitors that were causing fan to run backwards and trip compressor out on overload. Changed some loose spade connectors and foam cleaned condenser while there. Much more tolerable conditions to work in, 74 deg! System had been off all weekend, so these are pulldown conditions measured:
slt = 61
llt = 76
con sat temp/pres=92/180
cond discharge temp=98
con delta t=24
How do these numbers look? System seems to be operating good for an old dog on borrowed tim.