It was a test and the whole class failed
Atleast they didn't have to run the gas tight too far to pressure test the unit lol
Wait, was it 36" or 16" min distance, oh well house has been inspected long ago so no worries. :whistle:
Low loss fittings are to save fingers not enviroment - :grin2:
So is someone going to move the condenser or just say screw it? You were the last one there so its on you now.
I would have taken one look and not put my gauges on it but have customer sign off that it needs to be moved. Then pull the disconnect.
It took some nuggets to light that torch.