View Full Version : 3.0 ton HP with 2.5 ton Air Handler
02-01-2006, 11:10 PM
Is it ok to have a trane 3.0 ton heat pump (4TWX4036A) with a trane 2.5 ton air handler (4TEE3F31A)? I thought the heat pump was suppose to have less nominal tons then the air handler. Thanks.
dan sw fl
02-02-2006, 03:02 AM
Originally posted by dac350
Is it ok to have a trane 3.0 ton heat pump (4TWX4036A) with a trane 2.5 ton air handler (4TEE3F31A)?
No, so don't do it.
Use a 4TEE3F37A or 4TEE3F040A.
02-02-2006, 06:15 AM
That's an approved, ARI rated match BUT it only gets 13.00 SEER where the bigger air handlers will get 14 SEER and a higher HSPF.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.