View Full Version : hoshizaki ice flaker
01-16-2006, 08:52 PM
i have a problem with a hoshizaki ice flaker. when i got to the call the top of the barrel was iced up.the auger was still moving but can't produce ice cause the barrel is frozen. model#f-2000 mlh. the epr is factory set at 22psi r-404a. i washed out the barrel with hot water and got it going. BUT i know it will be a call back. i'll check on it later. what can cause the barrel to ice up. the ice seems to have alot of water doesn't look right. any ideas as what i can look for? the epr setting is at 24psi using r-507 and is running off a rack. i'm green on this things. please any info whould help.
01-16-2006, 11:05 PM
pull an OEM on this one for reference. Maybe it needs to descaled? Good luck.
01-20-2006, 07:44 PM
i have never worked on flakers what is involved in de scaling one just taking it apart and soaking in CLR??? the reason i ask is a friend need one fixed and it kinda looks like it needs to be descaled. tia
aprophet aka david
01-22-2006, 10:53 PM
i found the extruding head bearing with wear, the augar was also scrached. replaced and problem fixed.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.