View Full Version : Alarms
10-12-2011, 09:21 AM
I'm using chiller model # 30gt515676 and is made my life hell since last week. It usually stops and gives alarms # T112, T119, T173 & A152. Please send me details for these alarms so that I can get rid of them. Thanks
10-12-2011, 02:59 PM
Take a pic of the unit name plate because that doesn't look like any model number I've ever seen.
10-12-2011, 05:18 PM
Do you mean 30 gxn... Er. Gtn.. Something. Is it a carrier?
T112 sounds like a high suction superheat alarm from a carrier chiller.....
10-12-2011, 05:46 PM
T112 CIRCUIT A high succion superheat
T119 CIRCUIT B low oil press
T173 loss of communication whit EMM
10-13-2011, 05:16 AM
Thanks a lot to all for such a nice guidance.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.