View Full Version : Trane wsc060 not running unless...
06-01-2011, 10:14 AM
you bump in the contactor.....kind of like the carriers with the clo. This unit has .6 vdc from j6 6 to 8. Is that enough for cool call? If u bump in the contactor a fewmoments later the unit starts. According to the previous tech and the maint man. I cant duplicate that but they swear to it. Runs fine in test mode
06-01-2011, 12:15 PM
sounds like it doesn't have enough voltage to pull in but has enough to stay in. Is it using a conventional stat? If so, how long a wire run and what gauge t-stat wire.
06-01-2011, 02:35 PM
Yeah wiring is fine. 26v at the coil and I havent been able to duplicate problem so for now shrugging that one off. Replaced the tstay and now have 32v dc on 6 and 8 on j6 plug...ac running fine. I may have jumped the gun on posting....thanks for reply
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.