View Full Version : Integrate Trend into Honeywell AX
05-27-2011, 08:33 AM
Can a Trend control system be integrated into a Honeywell WEBs AX system? Are there drivers available for the Trend?
05-27-2011, 11:45 AM
There is a driver for the IQ2 & IQL series. I think infocon sells it. IQ3s have BACnet/IP and the newer IQEs are bacnet ms/tp.
What is the system made up of?
05-27-2011, 01:27 PM
They are using IQ220's...Sorry, I don't know much about Trend products.
05-27-2011, 02:20 PM
05-27-2011, 04:17 PM
Thanks orion242...I appreciate your help...
Am I correct in assuming that they will send me pricing in responce to my email to their "Contact Us"?
05-27-2011, 04:34 PM
I have never used them but I know a few people that have. From what I understand they will sell it to anyone.
One little bit of info you want to keep in mind....
Sounds like they are using the controllers serial port for the interface. You will likely want to plan on connecting this to a IQ22x controller as IQ21x serial ports only have access to that specific controller and not the whole system.
05-27-2011, 04:38 PM
Ok...I'll wait for their responce. Thanks again!!
05-28-2011, 04:38 AM
Trend now sell badged up Jaces, They call them TONN.
Thier version of workbench is called TESS and it has their developed drivers for IQ2 & 3.
These work very well insofar as point and Knob/Switch integration. It does not allow up/download or text comms.
Orion makes a sound point that you need a CNC port on something other than a 21X series outstation, this also applies to the Trend based Jace I'm fairly sure.
By the way, you cant run the Trend.jar file in the Honeywell version AX as it gets bombed out by a licence restriction. I thought I would give it a try.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.