View Full Version : TAC MR VAV ASC AX -100 I/stat base
05-03-2011, 09:07 AM
Does any why my I/stat base setpoint is on ( -100 ). I have a handful they started this. I Cleared memory ( NOVRAM ) ...Updated ASC and gave it a new file...still goes to -100 on base setpoint....has anyone else experienced this thanks,
05-03-2011, 03:18 PM
Sounds like you need to reprogram your i/stats. Contect to your station that the mr-vav is on then go to EDIT- CONTROLLER - MR FUCTIONS. Then find the address of the vav highlight it and hit istat. You should be able to fit that from there.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.