View Full Version : Excel 5000 actuator
07-06-2005, 05:28 PM
I'm trying to use a W7751G1003 actuator purely with 24 volts to drive it open and closed. I've taken the Excel board off and have RWWG for wires, thinking that R is hot and the two W's are common for power open and power closed. However, either that is not the case or I have a dead actuator. Or, the G wire figures in there somehow. While I understand the actuator is an ML6161, I don't know if special changes were made for the Excel module. The sticker shows 20-30VAC Rating, but that might be for the board to process. If anyone knows, I'd appreciate it.
07-07-2005, 10:40 PM
07-19-2005, 07:29 AM
The ML6161 actuator is a floating actuator (drive open/drive closed) and uses Red for clockwise rotation, Green for counterclockwise and the whites are common.
I am not sure about the W7751G controller you have, it shows up as an obselete Honeywell part number. I am looking at a W7751H controller and the wiring scheme is the same, although they used blue wire instead of green.
07-19-2005, 09:11 AM
Thank you for the information.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.