View Full Version : 30GXN225 water flows
06-23-2005, 12:23 AM
Hey guys anyone have a evap. flow chart for a 2 pass Carrier 30GXN225-A-72121 chiller. I got 2.5 lbs drop and need to know gpm. IOM says minimum flow is 256 gpm and I got a pump rated @ 215 gpm.
06-23-2005, 07:01 AM
2.5 psid isn't on the chart for that machine. Minimum pd is 8 @ 400 GPM.
See page 52.
06-23-2005, 10:27 PM
Thanks a bunch jrbenny that is just what I was looking for.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.