View Full Version : some pics. of some equip. we take care of
12-03-2010, 05:31 PM
check it out
12-03-2010, 05:48 PM
The Trane chiller has been or currently is being washed with condenser coil cleaner?
12-03-2010, 05:54 PM
right on that one........ a couple of plastic garbage bags would do wonders for those compressors in the long run and if that unit is 460V little acis on the windings in the fall let it sit with the snow melting till spring and baaaaaaboom:couch:
12-03-2010, 06:16 PM
we got one of dem choo choos with dual circuits, one circuit having a bad evap. it may be going away this spring. 350 tonner.
12-03-2010, 06:42 PM
Is that liquid receivers in the second picture?
12-04-2010, 07:40 AM
no, oil separator and it's scale on the compressors from spraying the coils with water when some fan motors went out over the summer, not our idea and we strongly recommended not to do it but it's the cust. machine not ours and they are paying the bills soo
12-04-2010, 07:34 PM
On the third pic, is that chiller down in a hole? Looks like a good opportunity for recirc of cond air.
Hows your head pressure in the summer?
12-05-2010, 12:39 AM
nice call, r134 runnin 270, we've gone thru like 6 motors this summer and on a good summer day, you can walk by the side the walls on and measure close to 140*f
12-05-2010, 12:54 AM
12-05-2010, 09:31 AM
awesome pics. I do residential and light commercial. I really wanna get into and learn commercial and industrial stuff someday.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.