08-10-2010, 11:02 AM
Hi, I'm new to this forum and I have limited knowledge of a/c. So, please bear with me. My a/c has been working fine until last night when we noticed a bit of water on the basement floor. I figured it was the condenser icing up. I checked the filters and replaced them because they were wet. I replaced them a few months ago so they were clean. I then let the blower run for about an hour and everything seemed fine when I turned on the a/c. The temp came down and some water was going down the drain. But a few hours later it started leaking again and the filters were wet. I've had the blower running all night and haven't started the air. BTW the vents in the house had sufficient air at the furthest vents. Could it be that the drain is partially clogged or that it needs refrigerant? I'm not sure because it seems as though everything is working properly even with the leaking of the water. The water is basically running down the back and side of the inside of the furnace. Thanks.