07-29-2004, 11:55 PM
Hey R-12 t-stat was set at 45 high event and diff. at 5. everything inside this cooler seems to be okay except I noticed that the condensate pan seems to be holding a little bit of water I assumed this was normal. head pressure was 180 and suction was 40, ambient about 85. Sorry the one thing I forgot to tell you guys was this unit never seemed to cycle off, I think the only thing that kept the coil from freezing up sooner was the defrost timer. Today I noticed that when I removed T-STAT bulb from Its factory position and moved it closer to the coil the solenoid closed and unit pumped down for about 2 min. and unit would start up again (cycling). I know this is not normal any help would be greatly apprieciated. This unit is two years old, I recently took this store over from another company and customer tells me that she has had problems with unit from day one.