View Full Version : Buderus G 115/4 with indirect
12-07-2008, 07:47 AM
12-07-2008, 03:34 PM
where is the stick shifter.... show us the circulation system(s)!!:cool:
12-08-2008, 10:03 PM
looks good though, i wish i had more experience with boilers.... someday....
12-13-2009, 08:00 PM
I love to see lots of blk pipe.. Only thing i see is you should run the dhw circ after an air scoop. Look at some pump away piping schematics and youl see why. Plus the advantages of using less vlvs..
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.