View Full Version : Teletrol Etrac on Tridium
01-07-2008, 07:39 AM
Has anyone had any success in integration of Teletrol eTRAC with Tridium
I have a few questions if anyone has done this.
I have done the IVAV with few problems, but can not get the eTRAC points themselves to show up. Only the Transciever shows up.
01-07-2008, 10:00 AM
Just a thought, but not every Bacnet 'suite' of devices supports the 'Discover'/'LearnDevice' Function. I recall with some Mitsubishi devices being sent Bacnet IP via a G50 gateway were not discoverable. I had to get a points list of the device with instance ID and create them myself.
I would try that in the first instance if you KNOW what the points are.
AX or R2, BTW?
Hope this Helps,
01-08-2008, 06:54 AM
I am on AX.
I did finally get it to talk. It appears that when etrac is configured using
Edifice through the ESC it starts the AI instance number at around 165 instead of 1. I had to go back to Edifice and poke around to find this.
I had just assumed that it would start at 1. The next hurdle is to get the AI temps to read something meaningful. Apparently the Transciever does not send out a corrected BACNet value even when set to read Degree F.
01-08-2008, 10:40 AM
Nice One - I guess now its just a question of Sums!
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.