View Full Version : rudd 2 stage furnace with single stage stat
11-29-2006, 10:24 AM
I'M HAVING A PROBLEM DIAGNOSING A RUDD FURNACE
WITH A SINGLE STAGE STAT. IT DOES NOT RAMP UP TO 2ND
STAGE AFTER 12 MIN. ANY IDEAS WOULD BE GREATLY. BOTH
STAGES WORK IF WI AND W2 ARE JUMPERED
11-29-2006, 01:15 PM
Single stage stat should be hooked up to W2 only.
11-29-2006, 07:28 PM
Take a look in the INSTRUCTIONS. I know thats a novel thought, and it will likely leave you without any kneeling pad, but sometimes you do what you gotta do.
I'm just busting your chops :)
11-29-2006, 08:36 PM
And if you still can't figure it out, call your local distributor and have him send out the regional tech rep :D :D :) :D
11-30-2006, 12:03 AM
Who will tell you to call your contractor back out and wire it properly. :) ;) :D õ¿õ
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.