View Full Version : carrier mini split question
06-25-2006, 09:46 PM
Model# 38BK009130 does anyone know what the maximum length of line set that can be used with this system?
06-25-2006, 10:07 PM
Maximum EQUIVALENT line length is 50' & maximum elevation difference is 30'. This system uses a mixed phase line set, metering device in outdoor unit. Line length is critical.
Powered by vBulletin® Version 4.2.0 Copyright © 2013 vBulletin Solutions, Inc. All rights reserved.